The range integrates the 4 REUSE reactors in a tight and raised PP enclosure to connect the S, M, L and XL sterilizers to the hydraulic gravity line. For each reactor, the maximum throughput was calculated for each quality class using highly constrained water, namely:
TSS = 35 mg/L
Transmittance = 50%
E.coli concentration: 100 000 UFC/100ml
Of course, if your wastewater leaving the WWTP is of better quality, the same reactor will be able to handle more flow, or you can choose the lower model.
Where to install REUSE manholes?
Manholes are to be installed at the outlet of the treatment plant, following the tertiary treatment, in order for the water to be treated to comply with the treatment requirements imposed on the treatment plant for the TSS, BOD5 and COD parameters.
On-site delivery by truck. The discharge is the responsibility of the customer.
Once the order has been placed, the above-mentioned period runs (excluding weeks 31 to 34 and 51 to 52) from the date of receipt of payment and validation of the project plan (including all the options requested in the case of special requests). As soon as the equipment is ready, it will be shipped to you. A road transport requires approximately one week to set up, it can take up to 3 weeks for a container depending on the destination.
Detailed technical sheet(s)
List of replacement parts and consumables
Under normal use conditions:
5 years on stainless steel reactor (materials and welds) except in the presence of a very corrosive environment (brackish or very salty environment, sea water, proximity of acid and corrosive products, use of hydrochloric acid).
2 years for the whole manhole and its components except for the UV lamp and the quartz sheath (consumable).
Defects and damage caused by natural wear and tear, external accidents, wrong assembly, improper maintenance, irregular use, inadequate storage, non-respect of the expiration date, intervention by a third party, or modification of the product not provided for or specified by the seller, are excluded from the warranty.
All the equipment in the REUSE range is equipped with upstream and downstream sampling ports fitted with flammable valves. Bacterial analysis should be done within 4 hours of sampling, on an average 24-hour sample kept in a cool place. The tests must be accompanied by a UV transmittance measurement at 254 nm as well as a TSS measurement.
REUSE manholes are delivered ready to be connected. They can be processed in 3 ways:
Completely covered (min. 100 mm overhang – max. -190 mm hydraudic wire)
Simply connect the hydraulic inlet and outlet to the flange collars, and connect the electrical cabinet to the mains (220V, 50/60 Hz)
UV lamp maintenance
The lamps are to be removed from the top of the reactor. Before any intervention, remember that :
UV lamps must be recycled according to the regulations of your country. Do not throw them in the regular or industrial waste, as they contain mercury particles.
When replacing a UV lamp, do not put your fingers on the glass. Cleaning the lamps with alcohol will remove any traces.
The light generated by a UV lamp must be carefully protected from direct or indirect view.
When replacing the UVC lamp, be careful not to put your fingers on the glass. Cleaning the lamps with alcohol will remove any finger marks.
When should replacement of wearing parts be considered?
It is recommended to change the UV lamps after 13,000 hours of operation, to maintain the guarantee of a sufficient level of irradiation. This replacement can be done at the same time as the Quartz UV sleeves (if they are damaged). When the sleeves are properly maintained, experience shows that a replacement every two lamps is sufficient (here every 26000 hours / 3 years for example)
How to recycle UV lamps?
That’s easy! Put the old UV lamp in the new lamp package and, for those using original Bio UV reactors, write “recycling” and then ship your used lamps to an approved recycling facility.